AS 080 - Automatic charging unit with time shift
The AS 080 automatic charging unit determines the charging rate for electric thermal storage heaters or electric floor
heating based on outside temperature and residual heat. The charging rate is shifted towards the end of the off-peak
period by means of a timer. The heating is switched on by activating a heater contactor by means of a relay contact.
Example of use
Single unit with time shift, residual heat measuring point, second thermal storage heater connected in parallel, and fan interlock.
(VDEW system 1).
|Rated Voltage||230 V / 50 Hz|
|Dimensions||45 x 105 mm|
|Breaking capacity||250 V~6 A resistive load|
|Power requirement||ca. 3 VA + breaking capacity|
|Permissible ambient temperature||0°C to +50°|
|Running time||22 hours|
|Self-holding||6 hours after beginning of off-peak period|
|Load characteristic||backward control|
|Mounting||top hat rail 35 x 7,5 DIN 50 022 without wall mounting|